The Fairchild 1500A features large supply and exhaust valves providing high forward and exhaust flows. A balanced Supply Valve seats minimises air consumption.
The output of the relay is the sum of the spring bias, set with the Range Screw, plus a pneumatic input signal. ( Po = Ps + K); where Po is output pressure, Ps is signal pressure, and K is the spring constant set by the Range Screw. The signal pressure exerts a force against the top of the Signal Diaphragm that creates a dow n ward force on the Diaphragm Assembly and opens the Supply Valve. Output pressure flows through the Outlet Port and the Aspirator Tube to the Control Chamber where it creates an upward force on the bottom of the Control Diaphragm.
When the setpoint is reached, the forces of the signal pressure and the Range Spring that act on the top of the Signal Diaphragm, balance with the force of the output pressure that acts on the bottom of the Control Diaphragm to close the Supply Valve.
When the output pressure increases above the setpoint, the Diaphragm Assembly moves upward to close the Supply Valve and open the Exhaust Valve. Because the Poppet Valve is closed, pressure flows down the Control Tube to the bottom of the Motor Diaphragm. This pressure keeps the Supply Valve tightly closed while in the exhaust mode. The Poppet Valve opens and excess output pressure exhausts through the Vent in the side of the unit until it reaches the setpoint.
250 psig, [17.0 BAR], (1700 kPa) Maximum
Flow Capacity (SCFM)
150 (255 m³/HR) @ 100 psig, [7.0 BAR], (700 kPa) supply & 20 psig, [1.5 BAR], (150 kPa) setpoint
Exhaust Capacity (SCFM)
40 (68 m³/HR) where downstream pressure is 5 psig, [.35 BAR], (35 kPa) above 20 psig, [1.5 BAR], (150 kPa) setpoint
Signal or Output Pressure
150 psig, [10.0 BAR], (1000 kPa) Maximum
Supply Pressure Effect
Less than 0.1 psig, [.007 BAR], (.7 kPa) for 100 psig, [7.0 BAR], (700 kPa) change in supply pressure
1" (2.54 cm) Water Column
-40°F to +200°F, (-40°C to +93°C)
Materials of Construction
Body and Housing: Aluminum
Diaphragms: Nitrile on Dacron
Trim: Zinc Plated Steel, Brass